Due to an onsite incident that happened with an operator on a job site today, please review this Safety Reminder. Pay attention to the minimum distances as well as what emergency procedures to follow in the even you do come into contact with power lines.
OSHA has established standards for the safe operation of cranes near power lines.
Line Clearance Distance
29 CFR 1910.269, OSHA’s Electric Power Generation, Transmission, and Distribution standard, limits crane operations to a minimum clearance distance of 10 feet from power lines and related equipment energized up to 50 kilovolts (50,000 volts). For power lines and equipment energized at more than 50 kV, the distance is 10 feet plus 4 inches for every 10 kV over 50 kV.
Safe Working Clearance Distance
OSHA’s minimum line clearance determines only the closest distance that any equipment or material can get to an overhead power line. It does not determine the safe working clearance distance. The safe working clearance distance is determined by adding a crane’s furthest reach, including the extension of any load, to the line clearance distance. For example, if a crane with a 100’ boom is working near a power line that has a line clearance distance of 10’, the crane should be placed 110’ from the power line. A 100’ crane located 50’ from a power line still has the potential to come in contact with the line. The safe working clearance eliminates this risk and should be used whenever possible.
Under no circumstances should equipment or personnel be closer than OSHA’s line clearance distance unless the utility has de-energized and visibly grounded the power lines and informed the appropriate personnel that the lines no longer pose a threat.
Contact with Power Lines
If the crane or mast comes in contact with a power line, the operator should swing the boom into the clear. If it is necessary to leave the equipment, anyone on the machine should jump entirely clear of the unit. Keep your feet close together and jump so that both feet hit the ground at the same time. Walk away in a small-step shuffle because a large amount of electricity flowing into the ground can create differences in electrical potential — enough difference to actually shock anyone whose feet are too far apart. Once clear of the equipment, do not return for any reason until the power line has been grounded and/or determined to be safe by the electric utility or owner of the line. Prevent personnel from touching or approaching the equipment.
All employees should be trained regarding safety-related work practices and procedures as required in the Electric Power Generation, Transmission, and Distribution standard.